Bool Scheduler Basic (T17)
Time scheduler bool, basic
FB : LIB.HVAC.V1_0.T17_BOOLEAN_SCHEDULER_BASE := (TPGVALUE := [(STARTTIME := 0, STATE := FALSE),
(STARTTIME := 210, STATE := TRUE),
(STARTTIME := 420, STATE := FALSE)],
Time scheduler basic is a source of a binary signal which changes according to a weekly schedule with maximum 42 events (changes of state). This scheduler doesn't support exceptions. Exceptions are implemented in T17_BOOLEAN_SCHEDULER.
||Date and time in case that other date and time than system date and time shall be used
||Output value if en=false
||Current time scheduler state
Description of internal structures
||Current state of the time program
||Minutes from the beginning of the day
The time scheduler basic compares current date and time with the definition table and sends the actual state to the output. The output is either true or false. The time scheduler can be edited from Idekit Studio or HMI - LCD display, web interface, touchscreen, SCADA or another client).
Time scheduler is used to enable plant operation according to the operating hours plan, for night depressions, etc. (Use T19_INT_SCHEDULER for multistate output, and T18_REAL_SCHEDULER for direct output of analogue values.)
The image illustrated switching between day and night heating curve. At the daytime the scheduler output is on TRUE, at the nighttime it is on FALSE.
In the editor, the scheduler plan is set up to be TRUE from 6:00 to 22:00, and FALSE otherwise: